IEC 61000-4-11 and 61000-4-34 are a matched pair of IEC standards that both say the same thing: equipment must tolerate voltage dips on the AC mains.
Both standards specify the same depths and durations of voltage dips, and explain how to apply these dips to single-phase and three-phase equipment. 61000-4-11 applies to equipment rated up to 16 Amps per phase, and 61000-4-34 applies to equipment rated at more than 16 Amps per phase; otherwise, the two standards are essentially identical.
PSL was deeply involved with developing and writing both standards. The PSL Industrial Power Corruptor is essentially the reference design for test equipment specified by these standards. Although these standards are similar to the SEMI F47 standard, they use slightly different dip depths. These standards also make the three-phase testing vectors much clearer than SEMI F47.
A typical IEC 61000-4-11 voltage dip (top) and how it affects a power supply (bottom).
Just like SEMI F47, this problem was fixed by increasing the size of a capacitor, at a cost of a few dollars.
Insert a voltage dip generator in series with the mains cable of the equipment under test. Use the voltage dip generator to create the voltage dips specified in the standards, and verify that the equipment under test works properly. That’s all there is to it!
PSL can help you with on-site certifications services, or we can work with you to provide a third-party certification of your own testing – see our Testing Partner program. For smaller products, testing at PSL’s lab can be the lowest cost approach.
IEC 61000-4-11 and 61000-4-34 are a pair of standards that set the requirements for voltage dip immunity. 61000-4-11 is for equipment that is rated at 16 amps per phase or less, and 61000-4-34 is for larger equipment.
Power Standards Lab
980 Atlantic Ave.
Alameda, California 94501
US: 1.888.SEMI.F47 or 1.888.736.4347